CECA joins the Canadian Federation of Independent Business Coalition for Small Business Tax Fairness
CECA Strategic Planning Session
National Apprenticeship Conference Theme Partner AnnouncedAnnonce du partenaire du thème de la conférence nationale d’apprentissage/
WHMIS IS CHANGING
NTCCC FEDERAL PROMPT PAYMENT LEGISLATION
Promoting Careers in the Electrical Contracting Business through Student Chapter Engagement and Research on Energy Efficient Projects
Calling on Everyone in the Construction Industry - Show Your Support for Bill 69, the Prompt Payment Act
The Government of Canada has issued a Request for Proposals - Le gouvernement du Canada a lancé und demande de proposition
NECA POST- CONVENTION TOUR
Training Based on the Upcoming Z463 Guideline - Maintenance of Electrical Systems - Scheduled Across Canada
Tax Savings for Tradespersons
RECALL - Ceiling-mounted light fixtures
Building Information Modeling Training & Implementation Seminar/Webinar - March 7, 2012 - Toronto
Canadian Electrical Code 2012
You are invited to a free webinar
RECALL - Siemens Q-Series Temperature and Humidity Sensors - 13-720
Thursday, January 31, 2013
In cooperation with the Consumer Product Safety Commission (CPSC in the States), Siemens is voluntarily recalling certain temperature and humidity sensors for schools, hospitals and other buildings due to fire hazard. You should stop using the product immediately, unless otherwise instructed.
This recall involves wall-mounted Q-series sensors that control heat, air-conditioning and humidity inside commercial buildings, hospitals and schools. The sensors come in three designs: a blank cover, a cover with a digital display screen or a cover with a digital display screen and door. The sensors are either white or beige and have a Siemens, Talon, Staefa Control System, Staefa Control System/Talon logo, or no logo. The recalled model numbers begin with QAA and QFA, and one with SB1. They are:
QAA 2060, QAA 2063, QAA 2072, QAA 2073, QFA 2000, QFA 2001, QFA 2060, QFA 2071, QFA2072, QFA 3000, QFA 3001, QFA 3060, QFA 3071 and SB1-0834
The model number is located on the sensor’s circuit board inside the unit. The units were sold by Siemens sales offices, partners, resellers and installers from June 2007 through August 2012 for between $200 and $400. They were manufactured in China and the United States.
You should look to see whether your sensors are currently operating on an AC power source and, if they are, you should immediately have the recalled sensors converted to a DC power source. Consumers should contact Siemens to schedule the installation of a free replacement sensor. Siemens is also directly contacting owners of the recalled sensors.
Customer contact information for Canada:
(855) 899-9937 - Phone
(855) 870-7305 - Fax
or CLICK HERE to visit them online.